In the horizontal system heating can not be fully warm all the rooms of the house. The heating system runs with your hands natural circulation, since this is sufficient circulating pressure. Since the stack of these building has a height of not less than 10 m, the boilers can run on any fuel. Recommendations on installation and operation of water heating In conclusion, some recommendations for compliance of building regulations, which should be taken into account during installation, adjustment and operation of heating systems, made by hand. Equipment with firing furnaces (boilers, ready to heat registers, stoves) should be installed under the rules of fire safety, providing for the installation of these devices at some distance from building structures. For example, a distance of ceramic pockets of fire (stoves, fireplaces, boilers) should not be less than 100 mm – up to fire-resistant, 150 mm – up to inflammable and 250 mm – up to combustible construction. Chimneys should be placed so that the firing plant (boilers, furnaces, etc.) can be placed in close proximity to the chimney, as long chimneys reduce cravings.
Chimney height and diameter are accepted depending on the type of heating system and fuel used. Solid and liquid fuels warehoused near the boiler in compliance with fire safety rules. With commissioning of water heating system check the conformity of its design and technical specifications, the correctness of installation pipelines, installation of heating appliances and fixtures, the location of a culvert units, the lack of leaks in pipe joints, valves and fittings, the strength of attachment of pipelines and equipment, serviceability of the valves, the uniformity of heating of all the devices in the building.